Can I have one feed for two seperate 3 way switches?. It is living room lights and stairwell lights. The feed comes from the living room lights and ends in the double gang box. That double gang box has the stairwell 3 way switch in it also. Then (2) 14/3 romex( the travlers) goes to the other switches. So I have (2) 3way switches in a double gang box. I have the feed, a 14/2 romex that comes from a high hat in living room. and I have the 14/3 travelers in that box also. I am just confused about the feed coming from the high hats. Thanks in advance. I wish I remembered how to make a one line diagram.