Looking for interpretation of Article 430.130(A)(1) and (2) with respect to Branch Circuit Short Circuit and Ground Fault Protective device rating for single motor applications when a VFD is involved. The article refers to 430.52 which really addresses only manual motor controller and overload relay. If a higher BCP value is specified in the VFD manufacturer's instructions, can this override Article 430.52 and Table 430-52 since overload and short circuit protection is provided by the VFD? The VFD is UL Listed with higher BCP value than 400% of full-load motor current. This is especially true for single-phase input VFD with 3-phase output but applies to others as well.