Master Electrician Electrical Contractor 01752
- Marlborough, Massachusetts USA
- Electrical Contractor
You could also test it by using a traditional voltage tester like an Ideal 61-076 from hot to the EG on the receptacle or on the breaker. If it trips then you should be good to go.I'm positive there is a functional equipment grounding conductor. All the wiring is new.