So, I have a service device with meter about 250 ft from the main residence which also has 2 out buildings (or separate guest rooms). I have 2 rods at the service and 1 at the main residence plus 1 at each of the outbuildings. The residence is fed with 4 wire single phase (separate #4 copper ground wire). The AHJ is asking for 2 rods at the residence and at each outbuilding. Am I missing something? I've been doing some code digging and can't find anything but I could easily be missing it. I would just drive 3 more to make him happy but it's rock and not fun plus I'd need to replace all the wires to maintain them in 1 piece as he also insists. Am I stuck with his requirement or is he making something up?