Hey guys, question of the day. I'm doing a detached garage that will have two feeders going into it (House panel, and living space above garage.) This is all fed from the same service which is a 4 gang meter pack on the duplex, each feeder has its own 2" pvc. There's going to be a UFER once they pour the footer. However the state inspector is telling me I have to hit both panels with the GEC unbroken to UFER, I've never done a set up like this. Where is he getting this from?