- Sneads Ferry, NC
- Engineering Technician, Electrical Contractor
I have a contractor wanting to have unfused service conductors from pad mount transformer going to hand hol before MDP. Then, having fused feeder coming from MDP into the same hand hole. I don't like it. Is this situation in the code? I have found raceway being an issue, not junction boxes.