Come on man, we just went over this a few weeks ago. I am very hurt I guess you did not like my answer post #10I have project which utilizes USE cable as feeder fed from switchboard underground direct buried.
Can USE cable be used for direct buried? I looked at 338 but does not say
Please compare post #8 here to post #13 in the link. So where in NEC it says USE-2 is ok for direct buried either?Come on man, we just went over this a few weeks ago. I am very hurt I guess you did not like my answer post #10
I know I had some variation of below question prior but design has change a little and I am not sure about few items NEC 2014 code wise. Please see attached sketches which show cluster of apartment residential one is Top view and second is Elevation view. The cluster has individual buildings 1...forums.mikeholt.com
I dont follow. What exactly do you mean? I have three phase 208V upstream breaker is 1000A. USE is all AL direct buriedMany today are listed USE-2 / RHW. In that case, it can continue into a building within a raceway. Are there enough conductors for an equipment grounding conductor?