I am reviewing a new panel schedule design that has a three-phase 208V 30A ckt breaker. From my understanding each leg can handle 24A with the 80% rule from the NEC, that is why we installed a 30A breaker. So what should the VA load be on the panel schedule for each phase? A single-phase calculation (at 2880 VA per phase) or three-phase calculation (at 8636 VA per phase) ? I should know this, but having a brain freeze. I think 2880 VA per phase. So any help to unlock my mind would be appreciated!