Hi guys! First off I love this site and have found it so helpful! My question is this, I am currently on a job that is adhering to NFPA 2010 in SD, CA and the question has come up whether or not we can run the dry contacts (after the FA relay) through the BMS conduit into the VFD for shut down? Is this code compliant and more specifically is there a code section that discusses anything like this? In my opinion they are viewed as dry contacts and not FA wires, so mixing with BMS shouldn't be an issue right? Thanks in advance!