I’m getting mixed answers maybe you guys can help? I have 120 V lighting system in a commercial building that is going to have 0 to 10v dimming capabilities. My question is on running the 0 to 10 V wires in with the 120 V switch legs. I would obviously use 600 V rated wire probably an 18 gauge THHN. What do you guys think?