We have a 800 amp switch gear, we have to do a line side tap. My Question is do I tap before the CTs or after CTs. Poco wires come in from underground land on bussing on Double lugs with one of the lugs empty. Then the CTs then the main breaker. Do I have to tap between the CTs and the main breaker for the CTs to read. Or can I tap between the CTs and were poco lands on bussing. I want to land on that empty lug, but I’m not sure if CTs will read that way thanks.