I went to table 300.5 column 4. I’m just seeing if I’m missing anything but it’s pretty clear. Not sure if there is anything else. I’m just curious I’m running a 60 amp circuit to a shed and was going to install direct burial cable. I was wondering can I go 12” if I have that circuit on a 2 pole 60 amp gfci breaker?