I have no idea what it should say. I'm electrical, I ain't no architect. I build weapons....not targets.shouldn't it say 3668 on the plan instead of 3068 then?
Why on earth would it require GFI protection? It is above grade, on top of the slab.Have not seen any posts about GFI protection or box conductor capacity.