It depends on the wiring method, if the cable is an MC type then the support requirements of Art 330 would apply. If it is a nonmetallic type cable you may have to reffer to the manufacturers installation instructions.
Why would Article 330 not apply?
90.3 seems to state otherwise
LOL I just googled it and saw that :lol: Here I am thinking it is some sort of code or standard.