Why would we discuss your diagram? Where is the egc? The premise of your argument presupposes that it is convenient to install additional ground rods, yet not than the code required bonding conductors. Any of us can see that is false. You ignore any questions asked of you and only press your strawman theory forward. This is indicative of a person who is bieng intentionality obtuse.
Or, he is showing us what he is taught.
The earth connection improves service continuity and avoids damage to equipment and danger to human life.
CODE OF PRACTICE FOR EARTHING[/h]
Obviously, we don't use the above standard in the US.
The Indian Standard is an interesting document. I just glanced through it trying to figure out why Sahib is being so adamant about his theory.