just curious, is it possible that 2/0 Aluminum feeding a 300 amp service causes sufficient enough of a voltage drop so that HVAC equipment reports of 500% in rush and lights dimming and etc? and I know the utility company always downsize is their wire. everything in the system to the equipment is properly sized. all the terminations are tight from main disconnect on. no bluing or discoloration of any terminals.